for information on our open source copyright compliance visit our copyright Notices page.
This diagram below is showing you the jumper setting for setting up your dry contact inputs to the opto-isolated setting.
That jumper is a 120 ohm switch, as in some cases of Modbus integration 120 ohms is needed on the RS485 input, so that has been added.
We offer two types of expansion modules. The first is the E-sensor8 expansion module and it has 8 RJ-45 Intelligent sensor ports just like the ports on the back of … Read More
The E-opto16 dry contact expansion modules can only be used as inputs, just like the extra dry contact inputs on the secuirtyProbe8-X20. Yes, the ?opto? in the product name means … Read More
Yes, the expansion modules can be daisy chained together using the RJ-45 input and output ports with normal CAT5 Ethernet cable. There really is no limitation to the amount of … Read More
The maximum run length of the expansion modules is 1000 feet. This is not the total run length. This is between the base unit and the expansion modules, or from … Read More
Yes, you can reset the securityProbe 5E back to the factory defaults by clicking on the ?Clear All User Data and Restore Original Settings? button from the Settings tab >> … Read More
The destination SNMP TRAP IP is not set the TRAP settings. The community entered is wrong. The firewall is blocking the SNMP TRAP traffic. The send SNMP Trap option is … Read More
For changing the Traps to HP OpenView style, you need to send an SNMP command to the device given below: snmpset .22.214.171.124.4.1.38126.96.36.199.1.60.0 i X Where IP is the IP address … Read More