for information on our open source copyright compliance visit our copyright Notices page.
This diagram below is showing you the jumper setting for setting up your dry contact inputs to the opto-isolated setting.
AKCP securityProbe not sending SNMP traps. The destination SNMP TRAP IP is not set the TRAP settings. The community entered is wrong. The firewall is blocking the SNMP TRAP traffic. … Read More
For changing the Traps to HP OpenView style, you need to send an SNMP command to the device given below: snmpset .126.96.36.199.4.1.38188.8.131.52.1.60.0 i X Where IP is the IP address … Read More
My AKCP device not sending alerts. This most likely due to either your “Rearm” settings, or your “Continuous Time for Sensor to be in new Status before accepting new Status” … Read More
Can I use version 400x firmware on the securityProbe box (previous generation hardware that does not have the 4 expansion ports? Yes, all new firmware that supports the new hardware … Read More
Loose settings on securityProbe device if update the firmware? No, as long as you leave the sensors connected to the 8 RJ-45 Intelligent sensor ports when migrating to the newer … Read More
The new securityProbe 5E has all the functionality of the previous generation secuurityProbe, but is faster and expandable. This is what the 4 RJ-45 expansion ports on the front of … Read More
Many types of these adapters should work. However, we specifically tested two types of these and found that the models that have these two chipsets pl-2303 and FT232BM worked, so … Read More
AKCP securityProbe5E Modbus Jumper – what is it for? That jumper is a 120 ohm switch, as in some cases of Modbus integration 120 ohms is needed on the RS485 … Read More