for information on our open source copyright compliance visit our copyright Notices page.
This diagram below is showing you the jumper setting for setting up your dry contact inputs to the opto-isolated setting.
The maximum run length of the expansion modules is 1000 feet. This is not the total run length. This is between the base unit and the expansion modules, or from … Read More
Yes, you can reset the securityProbe 5E back to the factory defaults by clicking on the ?Clear All User Data and Restore Original Settings? button from the Settings tab >> … Read More
The destination SNMP TRAP IP is not set the TRAP settings. The community entered is wrong. The firewall is blocking the SNMP TRAP traffic. The send SNMP Trap option is … Read More
For changing the Traps to HP OpenView style, you need to send an SNMP command to the device given below: snmpset .188.8.131.52.4.1.38184.108.40.206.1.60.0 i X Where IP is the IP address … Read More
This most likely due to either your ?Rearm? settings, or your ?Continuous Time for Sensor to be in new Status before accepting new Status? settings. You can check these settings … Read More
Yes, all new firmware that supports the new hardware and expansion modules is backwards compatible and has been tested on the previous generation of the securityProbes.
No, as long as you leave the sensors connected to the 8 RJ-45 Intelligent sensor ports when migrating to the newer firmware, you will retain all your settings.
The new securityProbe 5E has all the functionality of the previous generation secuurityProbe, but is faster and expandable. This is what the 4 RJ-45 expansion ports on the front of … Read More